Cooling Equipment Efficiency Criteria
Air-Source Heat Pumps and Central
Air Conditioner Key Product Criteria
|Air-Source Heat Pumps||>= 8.2 HSPF/ >=14 SEER/ >=11.5 EER* for split systems
>= 8.0 HSPF/ >=14 SEER/ >=11 EER* for single package equipment including gas/electric package units
|Central Air Conditioners||>=14 SEER/ >=11.5 EER* for split systems
>=14 SEER/ >=11 EER* for single package equipment including gas/electric package units
*Energy Efficiency Ratio
Air-Source Heat Pump (ASHP)
An air-source unitary heat pump model consists of one or more factory-made assemblies which normally include an indoor conditioning coil(s), compressor(s), and outdoor coil(s), including means to provide a heating function. ASHPs shall provide the function of air heating with controlled temperature, and may include the functions of air-cooling, air-circulation, air-cleaning, dehumidifying or humidifying.
Central Air Conditioner
A central AC model consists of one or more factory-made assemblies which normally include an evaporator or cooling coil(s), compressor(s), and condenser(s). Central air conditioners provide the function of air-cooling and may include the functions of air-circulation, air-cleaning, dehumidifying or humidifying.
Heating Seasonal Performance Factor (HSPF)
This is a measure of a heat pump’s energy efficiency over one heating season. It represents the total heating output of a heat pump (including supplementary electric heat) during the normal heating season (in Btu) as compared to the total electricity consumed (in watt-hours) during the same period. HSPF is based on tests performed in accordance with ARI 210/2401.
Seasonal Energy Efficiency Ratio (SEER)
This is a measure of equipment energy efficiency over the cooling season. It represents the total cooling of a central air conditioner or heat pump (in Btu) during the normal cooling season as compared to the total electric energy input (in watt-hours) consumed during the same period. SEER is based on tests performed in accordance with ARI 210/240.
Energy Efficiency Ratio (EER)
This is a measure of the instantaneous energy efficiency of cooling equipment. EER is the steady-state rate of heat energy removal (e.g., cooling capacity) by the equipment in Btuh divided by the steady-state rate of energy input to the equipment in watts. This ratio is expressed in Btuh per watt (Btuh/watt). EER is based on tests performed in accordance with ARI 210/2401.
1Air-Conditioning and Refrigeration Institute. Standard 210/240 “2003 Standard for Unitary Air-Conditioning and Air-Source Heat Pump Equipment.”
As always, if you have any questions or are looking for a certified cooling company, then contact us today.
The main priority of our HVAC contractors is providing our customers with comfort, efficiency, and excellent service.
We can repair your system right away or add value and comfort to your home with one of our professionally installed systems.
Want to know more? Then read what some of our amazing customers had to say about us. Or leave a review yourself.
We guarantee that all the work performed by the techs at Efficiency Heating & Cooling will leave you feeling 100% satisfied.
Address: 4040 SE International Way
STE E105 Milwaukie, OR 97222
Hours: Mon - Fri: 7AM - 6PM
Sat - Sun: by Appointment